Reedley CA Heating and Cooling
Rare Services Heating & Air is the HVAC company to call in Reedley, CA for professional, hassle-free and enjoyable heating and cooling services.
Read our Reedley, CA reviews to learn more about what makes us the preferred choice in Clovis, Fresno, Kingsburg and the surrounding areas.
for Reedley, CA
Frank - Reedley, CA
Checked in with customer Removed and installed new (1) 20x25x1" and (1) 20x30x1" Set up and cleaned condenser coils, heat exchanger, flame sensor, heating compartment and controls Checked all safeties, verified inducer motor operation .35 amps good Checked all electrical connections and voltage, 246.7v high, 27.7v low good Verified blower motor operation, checked all contactors and capacitors. Note: spring maintenance , change (2) 35uf 440 round run capacitors. Capacitors tested ok, but rusted out, ready to change in spring Checked evaporator coil, used leak detector on front side of coils and pan Tested complete heating cycle, unit working good at this time Call complete
Installed an APCO-X Air filtering system on customers unit.
Air conditioner and furnace will not turn on. Check condensing unit - compressor is running, but fan is not. Check capacitor for compressor and condenser fan. Capacitor is good. Temp test on condenser motor housing - reads higher than should be. Split system unit needs new condenser motor. Quote sent to customer.