Kingsburg CA Heating and Cooling
Rare Services Heating & Air is the HVAC company to call in Kingsburg, CA for professional, hassle-free and enjoyable heating and cooling services.
Read our Kingsburg, CA reviews to learn more about what makes us the preferred choice in Clovis, Fresno, Kingsburg and the surrounding areas.
for Kingsburg, CA
The gentleman that came out was great
Ian - Kingsburg, CA
Came out did the work fast and was very professional. Had a great experience.
Pauline - Kingsburg, CA
We were very pleased with the thorough check our heating unit received this week as part of our contract.
Response from Rare Service Heating & Air Conditioning, INC:
Pauline, We are happy to hear that you were pleased with your maintenance. Thank you for allowing us to be your service provider. We appreciate your business. Rare Service Heating and Air Conditioning
Our AC Unitr
Pauline - Kingsburg, CA
We found the representative very polite and prompt. Also very friendly. Only issue we have is we discussed our thermostat and we feel it is still not working properly. We set the thermostat about one degree above the room temp so it will not come on often during the night, only to wake up and the AC is running, the temp has changed from what I set it, and we hoped this had been resolved.
Checked in with customer Installed new 20x25x1" Checked evap coils for leaks, none Verified condenser and blower motor operation Checked board and wiring Checked electrical 246.3 high, 28.1 low Checked compressor Complete wash of condenser coils Checked capacitors and contactor Verified good split temp 51.1/76.3'F Unit info on file Unit working correctly at this time PM complete
Checked in with customer Gave both filters to customer (2) 20x25x1" Set up hose, went to RTU#1 & RTU#2. Washed both condenser coils out Checked evaporator coils for leaks on both units Verified blower and condenser fan motor operation on both units Checked voltage on both units 246.3 high, 28.3/28.1 low Checked control boards and wiring on both units Checked capacitors and contactors on both units Both RTU#1 & RTU#2 tested in cooling, good split temps 75/ 51'F both good Cleaned top, sides and ductwork on roof PM complete
Checked in with customer. Checked and found all safeties and controls, found all okay at this time. Cleaned flame sensor, changed 20x30x1 filter supplied by customer. Blew out drain pan/electrical/burner compartment. Note: Recommend blowing out condensate drain line at the Spring maintenance. Note: condensate pan shows signs of rust. Took measurements and picture. Job Complete
Checked in with customer Brought in and installed (1) 20x30x1. Set up ladder, removed panels to access for p.m. Verified blower and inducer motor operation Inducer motor amps Checked all electrical, 124.3v high, 29.2v low Blew out and brushed heat exchanger and compartment, and control compartment Checked all wiring connections, board condition and proper indicated lights Tested unit on heating mode, operating correctly Inspection of condesate lines, pan and vents Cleaned wood deck below unit to remove loose insulation P.M. completed Unit running per manufacturer specifications
Checked in with customer Pulled (2) 20x25x1" filters from TS-113 and set on porch Started with East unit serial # 1715C07070 Checked electrical, 245.3v high, 28.9v low Checked contactor for putting, visual inspection, no burn anywhere Checked capacitor (35-5uf) good Checked all board connections for any loose items in wiring Checked transformer setting for 230v high Checked inducer fan motor, found motor not coming on Continued check from inducer pressure switch, rollout switch, high limit switch And found wire connector off at bottom of switch Tightened and connections inside fan compartment, no loose connections now Put unit in heating mode, verified inducer and blower fan operation Inducer at .56 amps & .57 amps, good Checked indoor evap coil for any leaks with sniffer, no leaks found. verified clean Using camera, checked heat exchanger tubes and baffels. Cleaned out with blower. Blew out electrical and blower compartment Verified proper operation and visual inspec
Air Conditioning and Heating - Perform maintenance on split system. Check compressors, motors, boards, connections, refrigerant charge, safeties, heating components, valves, burners and temp splits. Clean condenser and evaporator coils. Change air filters. At customer's request, changed batteries in 5 smoke detectors.Unit is operating properly and safely in accordance with Manufacturer's specifications.
Air Conditioning Service - AC unit tripped breaker - Turn thermostat on to cooling, check compresser and capacitor - both good. Check all wiring. See wire connecting to contactor to the common on capacitor shows signs of being burnt. Run new wire from contactor to capacitor with two new spade connections. Unit is now operating properly and safely in accordance with Manufacturer's specifications.
Air Conditioning - Perform maintenance on Lennox package unit. Check compressors, motors, boards, connections, refrigerant charge, safeties, heating components, valves, burners and temp splits. Clean condenser and evap coils. Change air filters. Unit is operating properly and safely in accordance with Manufacturer's specification.
Air Conditioning Repair - Lost Power in 2 units -- Check thermostats; both condensing units off; find power board that air handler units plug into was in off position - turn switch on. Units came on and started cooling house. Test units before leaving. Both units working properly and safely in accordance with Manufacturer's specifications.
Air Conditioning Repair - Perform survey on home to prepare quote for a new split system replacement. Send quote to customer for new split system installation.