Fresno CA Heating and Cooling
Rare Services Heating & Air is the HVAC company to call in Fresno, CA for professional, hassle-free and enjoyable heating and cooling services.
Read our Fresno, CA reviews to learn more about what makes us the preferred choice in Clovis, Fresno, Kingsburg and the surrounding areas.
for Fresno, CA
Diane - Fresno, CA
Great service and I trust the work done. Very reliable company.
Response from Rare Service Heating & Air Conditioning, INC:
Diane, We are very happy to hear that you were pleased with our work. Thank you for allowing us to be your service provider. Rare Service
Customer service + Professional work = Rare Service every time !
Alfredo - Fresno, CA
My technician was very professional and made sure I understood what he was doing.
Response from Rare Service Heating & Air Conditioning, INC:
Alfredo, We are pleased to hear that you were happy with our technician! Thank you for your feedback. It is a pleasure to be your service provider. Rare Service
Steve - Fresno, CA
Attentive and great!!
Danielle - Fresno, CA
My service technician reviewed my unit thoroughly and cleaned additional parts due to wear and build up over time. I was very impressed with his attentiveness to keep me updated and make sure everything was running well.
Shirley - Fresno, CA
I love your service. I am so glad I signed up for twice yearly check ups. Nice to know my unit is running well. It seems to run cheaper too.
Professional and friendly
Mark - Fresno, CA
Louis - Fresno, CA
Jim - Fresno, CA
They did everything I asked.
Excellent Service. Will Use Again!
Anonymous - Fresno, CA
Great AC/heater inspection and report for house in escrow. Tim explained everything in detail. Will use for service!
Vicki - Fresno, CA
Rare did a great job of staying in communication with me and keeping me updated on their progress. I highly recommend them.
Planned maintenance Performed PM on unit Found gas leak on unit, while investigating also found crack in heat exchanger. Turned gas off to unit and informed customer unit was condemned. Took measurements for new unit. Will provide customer quote for new unit. Job Complete
Planned Maintenance Performed maintenance on unit. Checked voltage 240V 1 Phase. Compressor amps 9.4 with a rating of 15. Condenser amps were 75 with a rating of 1.1 Cleaned coil. Changed Filter. Unit is running great.
Planned Maintenance Removed dirty 20x30x1" filter from hallway, installed new filter. Checked thermostat for proper operation Washed condensor coils complete. Now clean Checked ball safeties and wiring Checked voltage. 240.2v high/ 27.8v low Verified compressor and condensor fan motor operation Checked inducer and blower motor operation Blew out and cleaned all compartments including exchanger Checked control board for normal operation Checked contactor, capacitor and control wiring Tested unit in cooling, working good Split temps. 51'F / 69'F Unit working good at this time PM complete
Planned Maintenance Checked in with customer Changed bad filter with new. (1) 25x25x1" Set up, wàshed condenser coils, cleaned area around unit Checked All safteies and wiring Checked inducer safety and verified operation of inducer motor Verified operation and condition of blower motor and condenser fan motor Checked voltage 238v high/ 28.3v low Tested unit in cooling 49'F / 76'F split. Good Visual inspection and operation of entire unit PM complete
Planned Maintenance Set up, opened all panels needed to finish PM Checked for leaks with sniffer at evaporator coils and condensor coils Blew out and cleaned exchanger, all compartments and controls Washed out and completely cleaned condensor coils Verified compressor and condensor fan motor operation Checked all wiring and safeties Checked capacitor and contactor Note: need to change contactor, showing signs of burning and small putting Cleaned out condensate lines Checked gas valve and lines Made sure roof clean PM complete
Planned Maintenance Measured for new filter sizes (1) 20x25x1" (1) 15x25x1" Checked thermostat Cleaned and blew out entire compartment Leak sniffed evaporator, good Checked all safties and wiring Verified blower motor and inducer motor for proper operation Checked valve and heat exchanger Tested unit in heating Unit heating correctly at this time Moved hose to west side of home Washed entire condenser and coils Blew out and cleaned dual capacitor and contactor Verified good compressor operation and condensor fan motor operation Tested unit in cooling, unit cooling correctly at this time PM complete
Customer called and said unit was shutting on and off Checked in with customer and went right to thermostat. Thermostat was dim and needed to be changed. Received authorization from customer to change thermostat. Changed thermostat, test, all working okay. Checked entire unit 2 days prior and wiped down flame sensor and blew out compartment
Responded to a no cooling call, customers unit was blowing hot air Checked thermostat for proper operation Set to roof, opened all panels needed Found (4) high voltage wires disconnected Checked wiring diagram and followed to factory spec's Tested unit, unit compressor working good Verified blower fan operation and condenser fan operation Thermostat now has control on unit Call complete
Checked in with customer, gave customer 5 star paperwork to fill out Checked thermostat Replaced filters with new filters (2) 14x20x1" Checked all heating and safeties, found bad connections at limit switch Switch connections just needed to be cleaned Washed all coils Cleaned out control and heating compartment with blower Verified fan operation, and condenser fan operation Checked compressor and wiring Checked for leaks at evaporator coil Checked contactor and capacitors, good Ran test in heating and cooling, good Temp split good, unit temp dropped quickly Cleaned up, collected 5 star paperwork Service complete
Checked in with customer Line filter size, removed dirty filter and replaced with new (1) 20x30x1" Checked furnace operation Cleared out drain pan and lines Checked coil for leaks During test, inducer motor making a lot of noise like bearings. Would like just a price on replacing inducer motor Checked all contacts, controls and wiring in condenser Checked run capacitors, found one had blown. Will replace on separate WO. Ok'd by customer Checked compressor and wiring Verified condenser fan motor operation Washed all condenser coils inside and out Customer filled out all forms needed for 5-star program Service complete